Hello Gentlemen, there has been some discussion about proper sizing of the motor starter, overloads, conductors, fuses and raceway. Being that Shane and Jude are headlining the wiring and we do not want to endanger our building compliance with such a large load. I took the time to figure this out for the pickle.
I used the motor nameplate, http://i.imgur.com/NRd46.jpg
And entered it into the motor branch circuit calculator based on the current 2011 NEC http://www.electrician2.com/calculators/motor_ver_1.html
The end result is this, http://i.imgur.com/gvuFu.png
I do not have Shane's contact information so if anyone reads this and sees him please direct him here.