mcsteve wrote:I should have been more clear, the nameplate amperage was definitely around 26A at 240. Rules for large motors are a little odd though, so the other important numbers I forgot to look at are MCA and MOCP. MCA will define the wire size needed, and MOCP defines the required fuse or circuit breaker size. If it doesn't list MCA and MOCP, I should be able to calculate them from the tables in the NEC.
Sent from my HTC Vision using Tapatalk
otto_pjm wrote:We got priced out of the Pallet Racking, and Metal Bender, but got one nice and one questionable welding table and a few air tools. Luno and I will be heading to Mankato next Thursday to pick them up.
Users browsing this forum: orion and 2 guests